FRASER, Howard, H., Jr. (2300 Tucker Road, New Woodstock, NY, 13122, US)
TARAS, Michael, F. (5424 Springview Drive, Fayetteville, NY, 13066, US)
FRASER, Howard, H., Jr. (2300 Tucker Road, New Woodstock, NY, 13122, US)
1. A shell-and-tube heat exchanger with a plurality of tubes disposed in a shell and adapted to conduct a fluid to flow within; and a refrigerant supply means for providing refrigerant into said shell and contained within the volume formed by said shell and external surfaces of the tubes; wherein the cross-section of said plurality of tubes is elongated in the vertical direction.
2. A shell-and-tube heat exchanger as set forth in claim 1, wherein said refrigerant supply means is located at the bottom of said shell and further wherein a level of liquid refrigerant in said shell covers at least some of said plurality of tubes.
3. A shell-and-tube heat exchanger as set forth in claim 1, wherein said refrigerant supply means is located near a top of said shell and further wherein refrigerant is dispersed in a spray that falls downwardly over said plurality of said tubes.
4. A shell-and-tube heat exchanger as set forth in claim 1, wherein said refrigerant is in a liquid state.
5. A shell-and-tube heat exchanger as set forth in claim 1, wherein said refrigerant is a two-phase mixture.
6. A shell-and-tube heat exchanger as set forth in claim 1, wherein said refrigerant supply means is located near a top of said shell and further wherein refrigerant vapor is directed to flow downwardly over said plurality of said tubes to be condensed.
7. A shell-and-tube heat exchanger as set forth in claim 1 , wherein said tube cross-section is a racetrack in shape.
8. A shell-and-tube heat exchanger as set forth in claim 1 , wherein said cross-section of said tubes is oval in shape.
9. A shell-and-tube heat exchanger as set forth in claim 1, wherein said cross-section of said tubes is elliptical in shape.
10. A heat exchanger for receiving refrigerant flow from an expansion device and delivering refrigerant vapor to a compressor comprising: a shell fluidly communicating with both the expansion device and the compressor; and a plurality of heat transfer tubes disposed within said shell and adapted to conduct the flow of fluid; wherein said plurality of tubes are formed such that they are elongated in their cross-section.
11. A heat exchanger as set forth in claim 10, wherein said plurality of heat transfer tubes are horizontally disposed and further wherein said tubes are elongated in a vertical direction.
12. A heat exchanger as set forth in claim 10, wherein said heat exchanger is a flooded evaporator with refrigerant being received at a lower portion thereof.
13. A heat exchanger as set forth in claim 10, wherein said heat exchanger is a falling film evaporator and further wherein said refrigerant is received near its upper portion thereof.
14. A heat exchanger as set forth in claim 10, wherein said heat exchanger is a condenser and said refrigerant is received near an upper portion thereof and removed at a bottom of the heat exchanger.
15. A heat exchanger as set forth in claim 10, wherein said refrigerant is supplied in a liquid state.
16. A heat exchanger as set forth in claim 10, wherein said refrigerant is supplied as a two-phase mixture.
Tubes with Elongated Cross-Section for Flooded Evaporators and Condensers
Background of the Invention
 This invention relates generally to heat exchangers for air conditioning and refrigeration systems and, more particularly, to shell-and-tube heat exchangers with refrigerant contained inside in the volume confined between the shell and outside surfaces of the tubes.
 Vapor compression systems for cooling water, or other secondary media such as glycol, commonly referred to as "chillers", are widely used in the air conditioning and refrigeration applications. Normally, such systems have relatively large cooling capacities, such as around 350 kW (100 ton) or higher and are used to cool large structures such as office buildings, large stores and ships. In a typical application applying a chiller, the system includes a closed chilled water flow loop that circulates water from the evaporator of the chiller to a number of auxiliary air- to-water heat exchangers located in the space or spaces to be conditioned.  A shell-and-tube type heat exchanger has a plurality of tubes contained within a shell. The tubes are usually arranged to provide multiple parallel flow paths for one of two fluids between which it is desired to exchange heat. In a flooded evaporator, the tubes are immersed in a second fluid. Heat passes from one fluid to the other fluid through the walls of the tubes.
 Many air conditioning and refrigeration systems contain shell-and- tube heat exchangers. In air conditioning applications, a fluid, commonly water, flows through the tubes, and refrigerant is contained in the volume confined between the heat exchanger shell and outside surfaces of the tubes. In evaporator applications, the refrigerant cools the fluid by heat transfer from the fluid to the walls of the tubes and then to the refrigerant. Transferred heat vaporizes the refrigerant in contact with exterior surface of the tubes. In a condenser application, refrigerant is cooled and condensed through heat transfer to the fluid through the walls of the tubes. The heat transfer capability of such a heat exchanger is largely determined by the heat transfer characteristics of the individual tubes and their position in the tube bundle.
 There are generally two types of evaporator applications: flooded evaporators and falling film evaporators. In a flooded evaporator, liquid refrigerant is introduced in the lower part of the evaporator shell, and the level of liquid refrigerant in the evaporator shell is maintained sufficiently high so that all the tubes are positioned below the level of liquid refrigerant in the majority of operating conditions. As the heat is transferred from the water flowing inside the tubes to the refrigerant, the refrigerant is caused to boil, with the vapor passing to the surface where it is than drawn out of the evaporator by the compressor. In a falling film evaporator, the liquid refrigerant is distributed horizontally to a sprayer, located at the top of the evaporator and spayed so that as its falls, it contacts the outside surfaces of the tube bundle, the heat transfer with which causes it to evaporate. The refrigerant then flows by gravity from the top horizontal tubes to the bottom horizontal tubes while cooling the liquid flowing within the tubes.  There are a number of generally known methods of improving the heat transfer of a heat exchanger tube in the bundle by reducing an internal and external thermal resistance for the tube. One way is to increase the heat transfer area of the tube by way of placing a plurality of extended surface elements such as fins on the outer surface thereof. This can be accomplished by making the fins separately and attaching them to the outer surface of the tube, or by forming fins directly on the outer tube surface. Another approach is to roughen the outer surface of the tube so that the nucleation sites that are formed can improve the heat transfer characteristics of the tube surface. Obviously, the two approaches can be combined or superimposed in a single manufacturing process. Similarly, internal tube heat transfer characteristics can be improved. Also, as mentioned above, the tube spacing in the bundle becomes critical and has to be optimized.
 It is desirable to have heat transfer tubes with external heat transfer surfaces that have good heat transfer performance in condensing and evaporating applications as well as for the flooded and falling film evaporator applications.
Summary of the Invention
 Briefly, in accordance with one aspect of the invention, the performance characteristics of a heat transfer tube are enhanced by forming the tube
with a cross-section area that is elongated in one direction as compared with the traditional round tube.
 By yet another aspect of the invention, the tubes are orientated with their elongated axis positioned in a vertical direction. In this way, enhanced heat transfer characteristics are obtained.
 In the drawings as hereinafter described, a preferred and modified embodiments are depicted; however, various other modifications and alternate constructions can be made thereto without departing from the true spirit and scope of the invention.
Brief Description of the Drawings
 FIG. 1 is a schematic illustration of a prior art chiller system.
 FIG. 2 is a schematic illustration of a portion of a prior art chiller system having a flooded evaporator.
 FIG. 3 is a schematic illustration of a portion of a prior art chiller system having a falling film evaporator.
 FIG. 4 is a schematic illustration of the flow path of refrigerant bubbles in a heat exchanger of the prior art.
 FIG. 5 is a schematic illustration of the flow path of refrigerant bubble in a heat exchanger in accordance with the present invention.
 FIG. 6 is a cross-sectional view of a heat transfer tube in accordance with one embodiment of the invention.
 FIG. 7 is an alternative embodiment thereof.
 FIG. 8 is a further alternative embodiment thereof.
Description of the Preferred Embodiment
 Referring to Fig. 1, there is illustrated a general configuration of a typical prior art chiller 10 having refrigerant flowing in a closed loop from a compressor 12, to a condenser 14, to an expansion device 16, to an evaporator 18 and then back to the compressor 12. In the condenser 14 the refrigerant is cooled by transfer of heat to a fluid flowing in a heat exchange relationship with the refrigerant. This fluid is typically a cooling fluid such as water supplied from a
source 20. In the evaporator 18, water from a loop generally designated 22 flows in a heat exchange relationship to the refrigerant and is cooled by transferring heat to the refrigerant.
 Fig. 2 schematically illustrates a chiller 24 with a tube-and-shell evaporator operating in a flooded condition with all of the tubes 26 typically being below the refrigerant level 28 in a majority of the operational regimes and the refrigerant supplied at the bottom of the evaporator.  Fig. 3 schematically illustrates a falling film tube-and-shell evaporator 30 in a chiller system 32. In contrast to the flooded evaporator illustrated in Fig. 2, it is known that the refrigerant flowing from the expansion device 16 flows by a supply line 35 into the evaporator shell to a dispensing device commonly known as a spray deck 38 overlying the uppermost level of tubes 40. A recirculation circuit, including a recirculating pump 42, draws liquid refrigerant that has not been evaporated from the bottom of the evaporator shell through line 44 and delivers it through line 46 to the supply line 35, where it is again distributed through the spray deck 38. The recirculation system thus ensures that there is adequate flow to the spray deck 38 to keep the tubes wetted.
 As will be recognized, both the flooded evaporator shown in Fig. 2 and the falling film evaporator shown in Fig. 3 include heat transfer tubes that are round in their cross-section. Fig. 4 shows a plurality of such round tubes in a typical spaced relationship in the tube bundle for the flooded evaporator applications, with an indication shown in dashed lines of the path of refrigerant bubbles as they swirl around the tubes as they are formed, grow in size, and eventually rise to the top. Here, it has been recognized by the applicants that there are two phenomena that tend to restrict the free rise of the bubbles as they are formed in the nucleation process.
 First, assuming that the tubes have a diameter "di", a bubble 52 which is forming at the lowermost portion of a tube as shown is restricted from its upward flow until the bubble grows large enough to overcome the restrictive forces and moves a distance comparable to dj/2 in either direction before it can rise to the surface. Of course, bubbles forming at intermediate positions between the lowermost positions as shown and a position directly to the side of the tube, will be
similarly, but less, restricted in its upward flow. The point is, this restriction to upward flow of bubbles extends over a distance comparable to "di" in the transverse direction for each of the tubes in the heat exchanger. The larger the bubble dimension, the more surface area it blocks from the liquid refrigerant to come into a direct contact with the tube surface, which is detrimental for the heat transfer. Obviously, the turbulent motion of pool boiling will promote bubble separation from the tube surface, but this process will be suppressed and delayed to some degree in any case.
 The second phenomenon that tends to restrict upward flow is that of the limited lateral range of unrestricted corridors between tubes in the heat exchanger. This effect becomes even more pronounced at the top rows of the tube bundle, where refrigerant vapor quality and bubble velocity are much higher due to a number and size of the bubbles rising to the top. For the heat exchanger compactness (to have more heat transfer surface into a given volume), it is desirable to stagger the rows of tubes such that the distances between the tubes in vertical and horizontal directions are less the tube diameter, so alternate rows of the tubes overlap each other, as shown for adjacent rows 54, 56 and 58. It will, of course, be understood that as the tube diameter "di" is increased, the distance "li" between the centerlines of the adjacent tube rows has to decrease in a given volume and for a given tube count. The less restricted upward flow of the bubbles, as discussed hereinabove, is best accomplished by increasing the distance "li" and decreasing the tube diameter "di" that is impossible to accomplish for the round tubes without the heat transfer surface reduction and evaporator performance loss, as well as pressure drop increase inside the tubes and the corresponding power raise. Similarly, the tube count must be maintained at a certain level for the same purposes, with the higher tube count tending to decrease the distance Ii .
 Shown in Fig. 5 is a plurality of evaporator tubes 60 in accordance with the present invention. As is seen, their elongated (non-round) cross-section areas are aligned in the vertical direction to generally coincide with the direction of the upward flow of the bubbles, as indicated by the arrows. Because of the elongated shape, the tubes 60 can have identical or similar cross-section area as the round tubes 50, and therefore have similar heat transfer surface amount and pressure
drop characteristics and can carry the same volume of liquid to be cooled, but, as will be seen, the resistance to upward flow of the bubbles for these tubes is substantially reduced. That is, since the dimension d 2 is substantially less than the dimension di, the resistance to the flow of bubbles forming under the tubes is substantially less. Further, since the dimension I 2 is substantially greater than the dimension of Ii of Fig. 4, the transverse dimension of the vertical corridor between the tubes is substantially greater than that for the round tubes. The result is that the Fig. 5 embodiment allows for easier upward movement of the bubbles formed on the outer surfaces of the tubes, especially at the top rows, and therefore improved heat exchanger performance. Further, since boiling heat transfer characteristics are improved, the tube length and tube count may be reduced to save cost and downsize the heat exchanger. Obviously, water-side pressure drop characteristics are to be considered simultaneously with the heat transfer characteristics to balance the overall system performance.
 The advantages of the present invention as discussed hereinabove are equally applicable to flooded evaporators and to falling film evaporators as well as to condensers. In respect to falling film application, however, there are further advantages in using the heat transfer tubes with elongated cross-sections. In falling film applications, the refrigerant is dispersed from above the tube bank and tends to fall on the top surfaces of the tubes and run down the sides thereof. Generally, the lower surface of the tube is not effective in the heat transfer process. Accordingly, the elongated cross-section tubes provide more surface area over which spayed refrigerant comes into direct contact with the tube (i.e. over the topes and sides) than does the round tube. In other words, the round tube has more surface area of the ineffective bottom portion than does the elongated tube. These considerations are true for a falling film evaporator, wherein a liquid refrigerant is spread over the tube bank and for a falling film condenser wherein refrigerant vapor is distributed over the tube bank. Also, in the condenser applications, the lower portion of the tube becomes ineffective in the heat transfer process and may experience the refrigerant flow vertices or boundary layer separation conditions.
 The elongated cross-section tubes can take various forms as shown in
Figs. 6-8. In Fig. 6, the cross-section area of the tube is a racetrack in form wherein
the ends 62 and 63 are semi-circular in shape and the sides 64 and 65 are linear in shape. In Fig. 7, the cross-section area of the tube 66 is elliptical in form. In Fig. 8, the cross-section area of the tube 67 is generally oval in form. It will be understood, of course, that various other shapes may be employed so long as the tube is generally elongated in its cross-section in the vertical direction.  It should be understood that in addition to tubes made by the conventional methods the present invention is also applicable to tubes made by an extrusion process, such as those made for so-called minichannel heat exchangers.  While the present invention has been particularly shown and described with reference to preferred and alternate embodiments as illustrated in the drawings, it will be understood by one skilled in the art that various changes in detail may be effected therein without departing from the true spirit and scope of the invention as defined by the claims.
Next Patent: EXPANDABLE MEDICAL DEVICE WITH DIFFERENTIAL HINGE PERFORMANCE